– BAC FXT 200
– Previous installer (not CTM) did not install fill correctly and tower was spilling water out all over. Would not maintain required tower temps for chiller.
– Replace fill pack and metal supports. Install plates behind fans to eliminate direct pressure on fill.
– Tower now operates efficiently, with water loss down to acceptable evaporation.